Specification static T8 luminaries designed and configured specifically for K-12 educational facilities. Class Pack is designed to deliver recommended classroom lighting levels for instructional and AV activities.
Smooth hemmed sides and smooth, inward formed end flanges for easy handling. Lighter weight fixture allows easy installation.
Standard steel door frame has superior structural integrity with premium extruded appearance and precision flush mitered corners. Steel door allows easy lens replacement without frame disassembly (for lenses up to .156" thick). Powder-painted, steel latches provide easy, secure door closure. Superior mechanical light seal requires no foam gasketing. Integral T-bar clips secure fixture to T-bar system. Housing formed from cold-rolled steel. Acrylic shielding material 100% UV stabilized. No asbestos is used in this product.
Class Pack is packaged specifically for most K-12 facilities. Luminaires are packaged in packs of nine or 12 to reduce material handling and increase the efficiency of installation at the job site.
Nine-packs consist of three master and six satellite units with 11' whips prewired for labor-saving installation. 12-packs consist of four master and eight satellite units with 11' whips prewired for labor-saving installation. Optional emergency lighting operation is available.
Finish: Five-stage iron-phosphate pre-treatment ensures superior paint adhesion and rust resistance. Housing painted after fabrication with environmentally friendly, high gloss, 93% reflectivity polyester powder-coat.
A12 lens (.125" thick) is standard. A19 lens also available.
Standard ballast is electronic, thermally protected, resetting, Class P, HPF, non-PCB, UL Listed, CSA certified ballast, universal voltage and sound rated A. Luminaire is suitable for damp locations. AWM, TFN or THHN wire used throughout, rated for required temperatures. Ballast disconnect provided standard where required to comply with US and Canadian electrical codes.
Instant start: high ballast factor, step-dim ballast.
Program start: high ballast factor ballasts.
Satellite fixtures are supplied with 11' cable and molded plugs to attach to connector in master unit.
When emergency battery packs are specified, battery pack is installed into a single master unit per Class Pack. When ELG is specified, a single satellite fixture is configured as a four-lamp with instant-start ballast.
Suggested Replacement Products
Photometry & BIM
Request BIM Files
|Correlated Color Temperature||3500 K, 4100 K|
|Voltage Rating||120, 277|